I am trying to do a direct replacement of an already existing 3rd party pendant light. How can I terminate my existing hot, neutral, and ground wires into this pendant fixture?
Unlike their square multi-cell counterparts, the round fixtures do not have an additional compartment to terminate incoming power wiring. There is an IEC connection on the back of the pendant fixture where incoming power should land.
Please adhere to your local jurisdiction when performing the following task.
Terminate the incoming power wiring to a junction box. Connect an IEC cable to that junction box and secure to the IEC port of the Four Cell Pendant.
ArcSystem Installation Manual (page 18) - CLICK HERE