Echoflex Interface Not Powering On
Echoflex Controller or Interface is not powering on.
No LED indicators will illuminate on unit.
Description/Explanation of Issue
Either the unit is not receiving proper power or is internally damaged.
- Meter incoming power to the unit.
- If voltage is good, replace the unit.
- If voltage is not good, continue troubleshooting upstream to determine the cause and resolve at that point.