The information in this post is provided to assist in troubleshooting. Perform work at your own risk. ENSURE ANY POWER FROM DEVICES HAS BEEN DISCONNECTED BEFORE SERVICING ANY EQUIPMENT. If you do not feel comfortable performing the work, please contact us or your local service center. Be aware that ETC and its Affiliates are not responsible for any damage or injury caused by service of our products by anyone other than us or our authorized service providers, and such damage is excluded from the product’s warranty.
If I have an SC1008 Branch Circuit ELTS, can I use the 0-10 contactor to trigger a DEBC if there's a loss of power?
Steps to Solution
Electrically, this will work. The 0-10 contactor can be used to close the circuit when landed to the vout and common on the DEBC. However, it's up to the local AHJ to determine if that will still comply with local codes for UL 1008 and UL 924.
If local code allows, the wiring would be as shown in the image below: