0-10v Analog dimming uses DC voltage. ETC Fluorescent Option Cards and 0-10v Analog Gateways should be used with isolated 0-10v drivers to reduce the risk of damage. This means little or no AC voltage should be present on the 0-10v lines. While some small amounts of AC voltage can be handled, more than a few volts can cause damage to the option card or gateway electronics.
Damage caused to ETC product by mains voltage leaks on 0-10V control lines is not covered by warranty!
Checking for AC Voltage
Do not work inside of a live rack! When testing, the ETC rack / enclosure must be closed and 0-10v wiring must be removed from the enclosure.
In order to check your lines for AC voltage, you must un-land and remove the 0-10v wires from the ETC 0-10v card or gateway and test them outside of the ETC equipment / enclosure. A True RMS Multimeter is required for accurate readings.
Test for AC voltage between positive and negative wires as well as between each conductor and ground. Typically positive wires are Violet and negative are Gray, although effective 1/1/2022 Pink is the expected color for negative 0-10v conductors.
- Begin with the control circuit for the 0-10v driver de-energized.
- Verify that the 0-10v conductors are disconnected from ETC equipment and made safe - capped off with a wire nut or similar.
- Energize the control circuit for the 0-10v driver.
- Use a True-RMS Multimeter to measure AC and DC voltage on the 0-10v control wires from pole to pole and each pole to ground. If any measurement exceeds 20V additional voltage isolation is required or there may be a problem driver on the line. Do not connect 0-10v wiring to the ETC control card until this condition is resolved.
- Observe that all fixtures are full bright when control wires are open and that when shorted all fixtures on the circuit go to their minimum level. If some or all fixtures do not dim, there is a problem with drivers or field wiring. The ETC controller cannot cause or resolve this kind of problem.
- If all of the above tests pass, de-energize the driver circuit and connect the 0-10v wires to the ETC control card.
Here is a handy excel file for recording Voltage. 0-10 Measurements.xlsx
Same Document but PDF. 0-10 Measurements.pdf
Up to 15VAC from conductor to conductor or conductor to ground is acceptable, though less than ideal.
20VAC and higher will cause damage to electronics.
ETC was using the EATON model number RFI-010v-1 LC, part number 12512441 (ETC part# SGE1508), but it was discontinued by EATON in Nov of 2021.
A possible equivalent is the nLight nFLT2.
ETC has a 2-channel unit that 7187A1191 FLT-LV 2ch 0-10v filter designed for simple j-box installation.
There are 2 groups of 2 wire pairs wire tie warped separably. Each group is for a channel consisting of:
Purple (+10v) and Gray (Com) that goes to the Fixture Drivers.
Purple/White stripe (+10v) and Gray/White stripe (Com) that goes to the control device (ETC equipment).
Ground wire must be attached to earth ground or the unit will not properly protect the circuit.
For larger 0-10v installations with AC voltage issues, there are larger wall mount kits as well. The enclosure is the same size as a Foundry mini panel, approximately 16"x14"x4.9".
Model Part number Part Description FLT-LV 7187A1191 2 Channel 0-10V Filter Box, Knockout Mounted FLT8-LV 7187A1192 8 Channel 0-10V Filter Box, Wall Mounted FLT16-LV 7187A1193 16 Channel 0-10V Filter Box, Wall Mounted FLT24-LV 7187A1194 24 Channel 0-10V Filter Box, Wall Mounted