Some 0-10 fixtures have 2 control lines, one for Intensity and one for Color Temperature.
Description/Explanation of Issue
These fixtures need 2 separate 0-10 circuits on the flourescent/0-10 option card to allow the fixture to utilize both features. This means it needs to land on two separate positions on the Fluorescent/0-10 Option Card.
- If your DRD is not fully populated, you can land the second set of wires onto an unused circuit and set it to mode 4 wire flourescent. This will work even if the module in that position is an AFM.