I have several different runs of LinkConnect that all need to land inside of the ERn. How can I do this?
The ERn's Lon header has multiple pairs labeled A-B, allowing you to land multiple runs of Lon wire on the connector. Lon is polarity and topology free, so it does not matter which wire is landed on A, and which is on B. It is not recommended to land multiple conductors in one A-B pair on the connector. If you have more runs than will fit on the connector, it is preferred to land a short jumper cable on the connector, and use a WAGO to tie in the additional runs of cable.