Stage Pantograph Circuit Count
A Stage Pantograph is limited to a maximum of 16 single phase circuits at 20A. We are able to build a pantograph with up to 24 circuits at 20A; to achieve the higher circuit count the pantograph will need to be operated with a minimum load diversity of 50%.
The quantity of low voltage DMX and/or network cables we're able to include in a pantograph varies depending on the total circuit count.
A minimum 50% load diversity can be achieved by utilizing a maximum of 50% of the power capacity of the total circuits in the pantograph. 50% load diversity can be achieved by using all 24 circuits at 10A maximum, by using 12 of the circuits at 20A, or any circuit combination that uses up to 50% of the circuit capacity.