Unison Legacy Error Message Chart
Upon starting and during operation of your system, the control module will display messages to indicate system status.
|DISPLAY MESSAGES||STATUS||SUGGESTED SOLUTION|
|System OK||System operating correctly||None required|
|Backup Active||Backup look playing||Turn backup look off|
|Test DMX Off||Test menu active||Restore DMX in test menu|
|Errors Exist||1 or more circuits have specific errors||Scroll through error list|
If errors exist, use the right arrow button to scroll through the list of circuits and associated errors. Multiple errors can be seen by pressing [▲] or [▼].
Possible error types include:
|DISPLAY MESSAGES||STATUS||SUGGESTED SOLUTIONS|
|SSP_ERR||Indicates I2C error||Cycle power - Call factory|
|No DMX||DMX is not being received||Hook up DMX or turn on console|
|DMX ERR||Bad DMX packets being received||Verify DMX wiring and termination|
|No Zero||One of the phases has failed to detect zero crossing. System is likely inoperable.||Call factory|
One of the phases has failed to detect zero crossing. System is likely inoperable.
|Over Temp||One or more of the dimming modules has been shut off due to sensing of over-temp.||Make sure fan is running - Check rack filter - Check module input vents - Replace module.|
Rack is receiving insufficient voltage for initialized parameters.
Verify input voltage
|Voltage High||Rack is receiving excess voltage for initialized parameters.||Verify input voltage|
|Arch Failure||The control module has been configured as a CME/CMEd orCMB/CMBd and communication with the architectural processor cannot be established.||The control module must be configured as a dimming module in the [Rack] menu, or call ETC.|
|Bypass Active||A power failure in the normal power feed was sensed. Dimmers have been driven to full, bypassing all control.||Restore normal power.|
|CPU 01 - 06 Fail||A dimming processor in a -d module has failed.||Call ETC|