ArcSystem Pro Emergency Behaviour
The information in this post is provided to assist in troubleshooting. Perform work at your own risk. ENSURE ANY POWER FROM DEVICES HAS BEEN DISCONNECTED BEFORE SERVICING ANY EQUIPMENT. If you do not feel comfortable performing the work, please contact us or your local service center. Be aware that ETC and its Affiliates are not responsible for any damage or injury caused by service of our products by anyone other than us or our authorized service providers, and such damage is excluded from the product’s warranty.
Is it possible to choose which level ArcSystem Pro emergency fixtures go to when the sense feed is lost? On MultiCell fixtures, is it possible to choose which cells come on when the sense feed is lost?
No, these things are not possible. On losing the sense feed, emergency fixtures will always send all cells to 100% and there is no way to change this. The tick box in the configuration software labelled "Emergency Override" does not affect this behaviour.